Job Date: 6/26/2013 |
Job Type: Low Water Pressure |
Job Location: Beethoven St., 90066
Customer Symptoms:A landlord received complaints from multiple tenants in his building that the water pressure was very poor.
Issue:Although he attributed the first report as merely a problem with a single faucet in the apartment and had previously called a repairman to inspect the unit, after he received calls from every client, he realized that the whole building needed to be checked.
Resolution:The technician needed to narrow down the cause of the low water pressure. He first checked the water meter to ensure that it was turned on the whole way and that the repairman had not turned it back. He found that the meter itself was not completely on and mentioned this to the client. The client remembered that he had called a repairman to look at one apartment after he received the first call and realized that the repairman may have forgotten to turn it back on the rest of the way. The client thanked the technician for being thorough and narrowing down the cause of the low water pressure so quickly.